Florida Power and Light Company - More Ridiculousness
Check out this FPL repair job on a residential 200 amp underground service wire (see attached photo). We ran across this and figured that this shoddy repair work, clearly made by one of FPL trained professional technicians, is what ruined this entire meter socket. Sadly, this meter socket had to be repaired at our customers expense.
Look at the photo closely. I especially like the red zip ties that are attached to the wiring. What the H?!! I guess that when those zip ties burn off it would be a clear indication that more electrical tape needs to be applied.
Good job, FPL!
Review about: Fpl Repair Service.
Review #685513 is a subjective opinion of a user.